Engineered, Manufactured, and Shipped Directly to You
|System Model||2 Ton||3 Ton||4 Ton||5 Ton|
|System output||24,000 BTU||36,000 BTU||48,000 BTU||56,000 BTU|
American Dream Geothermal heat pump uses refrigerant filled copper pipe buried directly in the earth to harvest heat energy for your home or building.
Our direct earth coupled heat pump is one that has its refrigerant evaporator/condenser in direct thermal contact with the earth from which heat is either extracted during the heating mode, or introduced to during the cooling mode of operation. Conventional technology concerned with heat pumps relies upon the transfer of heat from the ground by means of a secondary heat exchanger system and working fluid, e.g., water, which is pumped to the geothermal unit located in the heated structure. The conventional heat pump has it’s own internal primary heat exchanger which extracts heat (heating mode) or rejects heat (cooling mode) from this water, which is then pumped back to the earth to be re heated. American Dream systems similarly use a ground coil system, however, the working fluid is a refrigerant (rather than water) and the copper ground loop is the primary heat exchanger. Such geothermal heat exchange is the most efficient and effective way of achieving heat exchange in heating and air conditioning systems, and especially heat pump type systems.The refrigerant used is freon which is unbelievably more effective. Since the ground temperature is relatively constant at 48 °F at a depth below the frost line, the available heat is constant. The elimination of the secondary earth heat exchanger (typically plastic in nature) and its associated working fluid reduces the temperature difference required between the ground and the evaporating refrigerant yielding a higher suction pressure than a conventional system under similar circumstances and thus a higher efficiency.
Many attempts have been made in the past to develop successful direct coupled heat pumps for residential and commercial uses. These attempts have failed adequately to meet a number of requirements associated with an economically and functionally viable system.
The American Dream Solution
The solution has been to start with a clean new concept and to design a unit from the ground up. We started by developing an evaporator system that would yield the best performance to pressure drop factor and which would impact enough area to maintain a minimum suction pressure above 40 Psig. The current horizontal ground loop comprises 350’ per ton of 1/2” OD copper tubing. A 3 ton system would have 3 such loops working in parallel during the heating mode. Refrigerant charge had been determined to be 5 lbs. of R-22 per loop. These 1/2” copper loops maintain sufficient velocity at all times to insure adequate oil return. During cooling mode the machine automatically selects one or more loops based on discharge pressure to act as the condenser. As the discharge pressure builds to a predetermined point the on-board computer selects the most appropriate combination of ground loops to dissipate the heat at the lowest cost to the homeowner. By intelligently controlling the manner in which the condenser is utilized our total system charge does not have to be altered nor does an excess charge have to be stored anywhere.
Fewer parts to the system Does not require a supply and return well. Does not require a well pump or circulation pumps. No water heat exchanger and associated valving to corrode, freeze and break. Freon filled copper tubing oppose to typical water heat exchange More Efficient The direct expansion principle allows the refrigerant to come directly into contact with the earth, separated only by copper tubing. During winter,maximum heat transfer takes place at higher temperature than conventional ground loop technology without the maintenance and electrical cost of circulation pumps.
American Dream systems can be installed in a more confined area than a conventional groundloop system, primarily because the heat exchanger coil is much more efficient at transferring heat to the refrigerant than a plastic earth exchanger. Normal loop lengths for our machine are nominally 200’ per ton as opposed to 450’ to 500’ per ton for a plastic earth exchanger. Similarly, vertical systems require only a 3” bore hole to a normal depth of 75’ per ton.
Unlike ordinary air conditioners or heat pumps, there is no noisy outdoor unit to disturb your outdoor environment or your neighbors. WaterFurnace geothermal systems are designed and constructed for “whisper quiet” operation, similar to your refrigerator.
Unlike air conditioners and heat pumps, geothermal systems are installed indoors (like your refrigerator), so they are not subject to wear and tear caused by rain, snow, ice, debris, extreme temperatures or vandalism. Geothermal systems have proven to be very reliable and require less maintenance.